View available Temtrol files, documents, and brochures to download with additional product information relating to coil replacements.
View a specific product/brand name to review their standard terms, conditions, and warranty information relating to product coverage & responsibility.
When mistakes are made and the hands change, stay calm. You can make water coils work without making new coils. Temtrol determines left or right hand by looking at the entering air side of the coil, so the air is at your back.
If the coil is to deliver its full capacity, both its internal and its external surfaces must be clean. The tubes generally stay clean in pressurized water systems. Should large amounts of scale form when untreated water is used as coolant, chemical or mechanical cleaning of the internal surfaces at frequent intervals is necessary.
First determine the type of coil: hot water, chill water, steam, DX, condenser 2 Stand in the air stream & determine the location of the supply & return headers. Meaning is it a same end connected (supply & return header) on the same end; or opposite end connected with the supply on one end and the return on the other.
A coil that is used to heat air with steam must be able to continuously change the state of the water vapor (steam) to a liquid condensate by removing from the steam nominally 1,000 BTU per pound.